Quick Set Series Focus: Battery Mode and Battery Parameter Settings
How: From the from MTS-Com Front Panel Administrator Menu
Select DC Limits – Screen will display the High and Low threshold limits for DC output parameters.
o Press the DOWN arrow button twice to move the cursor to the Ext Equipment screen
o Highlight BATT/LOAD (default is Load) and press ENT once to select the field (background will darken against text).
o Press the UP or DOWN button to change the selection to the desired system type and press ENT once to accept the new selection.
o Press ESC once to return to previous sub-menu and proceed with battery charge settings outlined below.
Select BATT SETTINGS and the screen will display all necessary inputs for battery maintenance and monitoring.
o Parameters Include:
Battery Voltage for Float and Equalize modes
Current Limit to battery
Battery Capacity in AHr
Auto EQ Cycle (off / on)
• % Capacity for EQ mode
• Cycle Days to perform EQ mode
• Time Limit for EQ mode
Center Temperature for Compensation
Temperature Compensation Coefficient Factor
ESC to top level and exit Admin mode.
Additional Document References:
1. TB-027-18 Revision 0.1
a. Section MTS130, page 25-26
Search “Quick Set Series” for more application insights.